CFP 8 Zone Repeater Panel
- Can be used to repeat the functions of a master CFP standard or AlarmSense 2-8 zone fire panel at remote parts of site (e.g. all potential fire service entrances).
- Up to 8 repeaters per CFP master.
- Includes its own Mains power supply that requires its own standby battery supply.
- Provides the user with access to all AL1 and AL2 functions.
- Master/Repeater communication achieved using CFP761 network driver cards (one CFP761 is supplied with the Repeater, an additional CF761 card is required at the master CFP).
- Communicates over screened two-wire fire resistant cable.
- Total repeater network cable length should not exceed 1KM.
- Attractive flush or surface mountable plastic lid and enclosure – no bezel required.
|Internal power supply|
|Max battery size and type|
|Max. network cable length|
|Product dimensions (mm)|
|Construction & finish|